IEC MV, XLPE Insulation, CWS, SWA, PVC -KM
Multi-core XLPE-insulated cables with PVC sheath
StandardsInternational : IEC 60332-1; IEC 60502-2
National : BS 6622; EP-MS-P4/S3-030
These power cables are used for electricity supply in medium voltage installation system. They are well adapted to underground use in industrial application where chemical and mechanical protections are needed. This group is complying with IEC and Kahramaa specs.
Stranded bare copper class 2 acc. to IEC 60228 or equivalent
Triple extruded Inner semi conductive layer - Cross Linked Polyethylene 'XLPE' - Outer semi conductive layer
3. Metalic Screen
Copper wire screen with open helix copper tape "105 sqmm"
4. Inner Sheathing or Bedding
Galvanized Steel Wire Armour "SWA"+NCWB Tape under and above the armour layer
6. Outer Sheath
Polyvinyl Chloride 'PVC'
- Flame retardant : IEC60332-1 or equivalent.
1.Air Temperature : 30 Deg.
2.Ground Temperature : 20 Deg
3.Soil Thermal Resistivity : 1.5 km/w
4.Depth of lay : 0.8 m
All dimensions have tolerance +-7 %
no. of cores x conductor size mm2 Cu/XLPE/SWA/PVC Voltage grade V Standard MADE IN QATAR QICC - Nexans Year Meters
Custom marking available
|Conductor flexibility||Stranded class 2|
|Conductor shape||Circular compacted|
|Material of the inner semi-conductor||Semi-conducting compound|
|Insulation||XLPE (Cross-linked Polyethylene)|
|Material of the external semi-conductor||Semi-conducting compound|
|Screen||Copper wire + copper tape|
|Armour type||Galvanized steel wires|
|Outer sheath||PVC compound|
|Mechanical resistance to impacts||Good|
|Flame retardant||IEC 60332-1|
|Bending factor when laying||30(xD)|
|Bending factor when installed||15(xD)|
|See all products|
Products and services
Docs and info
Note: On request we are delivering three single core laid up cables on one drum